The device is designed for industrial use for assembly into premises with limited access (electrical switchboard).
Wiring up must be carried out by an individual with knowledge of the regulation No. 50/78 Coll.
The supply is designed for assembly into switchboards by attaching either to a mounting plate by means of M3 screws or on to a DIN rail. The mounting plate and DIN rail must be properly grounded in accordance with valid standards. The source must be located in such a way so as not to prevent air circulation necessary for cooling purposes.
Conductors must be wired into labelled terminals in accordance with valid standards. Terminals are only designed for connecting cooper conductors of max. diameter 2.5 mm2 and do not serve for switching devices under voltage.
For accumulator connection is recommended using only connection conductors producted by RACOM. This conductors contain temperature sensor and safety fuse F6,3 A. Without the original connection conductor will not be optimized charging process depending on ambient temperature!
The producer does not recommend to change accumulator poles when wiring up.
Color cording of low voltage conductors must comply with the requirements of respective standards.
The producer recommends to protect the 230 V AC input by circuit breaker of 6 A rated current with characteristics C.
The source must be disconnected from the battery when replacing fuses. Only the same types of fuses with the same current rating can be used for replacement.
When using the device as a source of SELV voltage the extra low voltage side must be electrically and spatially separated from low voltage conductors.